UK - MaidenheadCLS Data centre cooling maintenance
Today we took down the free air cooling handlers sequentially, servicing and upgrading them in time for the warmer summer months. No impact on any services or customers. We have added additional holding tanks in the return loop, and added 40 more sensors for temperature and leak detection, bringing the total to 120 sensors. Soon we will be ready to chill the intake water with mechanical/compressor cooling, further increasing the load trigger before the main chillers are activated.